You should not fill both, Client and Server configuration. Only one. In this case for Server.
We managed online session today and established TCP Online communication between U90Ladder and PLC.
Unfortunately I have no LabView experience and cannot help with it.
May be somebody did it? If yes - please share experience.
*I found by Google ( search for "labview modbus tcp read"):
"Basic MODBUS TCP/IP Read Holding Register using LabVIEW"
May be this will help.
I am new to Unictronics and have written an application PLC + HMI with 10 Screens.
During test a trend is started, 2 feeds, datasampling (SD card) Sometimes the error HMI application overload popups.
Found in the system tags the execution tags, and one is the Pusage tag. It keeps at >90% and sometimes even 100%, Even without VNC/ Webserver or the trend is running
Is the overload error related to this?
Is this normal an is there a way to reduce panel usage? For example in Siemens you can set the tage update rate.
Thanks in advance!