Want to share a UDFB? Here's the place! NOTE: This page contains files and links to items developed by third parties. Unitronics bears no responsibility for any consequences of accessing and using any third-party items of any kind.
There is no way to do a simple mirror. However, my interpretation of your ask is that the extra IO is being added to the 1210 that is already there.
In that case, you could consider running Remote Access or Remote Operator via a dedicated mini puter and touch screen, linked to the existing 1210. (Various methods of the connection available) This would/should give you all that you want, and would likely be cheaper anyway.
Once again, I ran into a roadblock where the manufacturer's tech support people couldn't tell me the necessary parameters to set up the EIP communications with a Unistream. They could only direct me to an EDS file online.
With past experience, the EDS file print out, and some trial and error I found the following parameters to work:
Input Assembly Instance: 100, size 24
Output Assembly instance: 150, size 10
Configuration Assembly Instance : 5, size 0
Check the box for "Use Run Idle for O2T" on the Output Assembly Instance
For the Creators: Is there any plan to eventually be able to install EDS files through Unilogic? This would greatly speed up the development time.
@Ofir I tried to send the two emails with the ethernet connection, with one file each, two diffents ".jpg"; in the first the size of file is 395 KB in the second 1.5 MB.
There is no problem with of this connection type.
My modem doesn't work for this type of application. We will use another type.
I have some programs that use the Transfer >PLC>PC or Transfer> PC>PLC, and it does make more sense.....
Now, A-B uses the Download to PLC and Upload from PLC contention, so it must be correct........🤔