Search the Community
Showing results for tags 'HSO'.
tbalogh posted a topic in Vision & Samba PLC + HMI Controllers & VisiLogic SoftwareHi, I'm a new user and I've been trying to get a PTO pulse signal from one of the high speed outputs of my V130-33-TR34 to send to a stepper motor driver. I just got the PLC so it's set to default jumper settings. I pretty much followed the webinar on the Unitronics site and I'm pretty sure I did the wiring right (pin 1 on the transistor outputs to driver, pin 5 to PLC ground). Hooked it up to an oscilloscope and I don't get anything out. When I run the PTO move command, it turns the MB on for "PTO Move Success." Tried going into the HW Configuration and trying to get a PWM signal out
What does a status message of 1000 mean in the PTO Configuration block? In the help file it only lists messages as having numbers 0-8. I am using a V130-J-TRA22.
Hello All, I apologize for the VERY basic questions I am about to ask but I am new to using a PLC to control a stepper motor. I have the drive and motor. I read the information included in Visilogic. I am still confused. I hate to ask but can someone please provide me with basic program to control the stepper drive. I want to provide an RPM and FWD/REV bit. I will answer any questions and will be monitoring this thread constantly over the next few days. Thank you in advance. Again, I apologize for such basic information but once I have a decent example I should be able to pick
I am using a V130-T4-TR6 and need to verify some information on the HSO output that seems contradictory between the tech spec and the V9.5.0 help file. Per the tech spec, the HSO freq. range is 5Hz to 200kHz. According to the help file, a value of 0 can be used but is not mentioned in the tech spec. It seems that the 0 value is used for a constant "ON" signal. Is this value available in the V130 and if so, please verify its function.