Search the Community
Showing results for tags 'rtu'.
Hello, I have JZ20-J-R16, and I want to read values from output 1 on labview, but I just have a problem in trying to do it. My PLC doesnt have an Ethernet port, I can just connect it by means of a USB, or com port to my PC. So if I wanted to read from this PLC on labview by means of RTU communication, can someone please give out an easy code to do that (to configure the PLC, and thus assign the addresses to each port)? And if I bought an external mode that contains an Ethernet port and connected it to my PLC, would I be then able to communicate by means of TCP through labview? I need help o
Does anybody know if Vision controllers (ie V130) support Modbus TCP or do they support the Modbus RTU over TCP implementation. The difference is that the first follows the original Modbus TCP frames (ie no CRC) while the latter encapsulates the serial RTU framing sent over TCP media. Which one is supported by Vision and the other Unitronics controllers?
Hi, today in our company we received an ultra filtration system that comes with a V1040 on it. We've never had worked with an unitronics system before and we are trying to communicate the plc via modbus rtu over rs485 to work with our network. We configured the com port of the plc to work with rs485 as it was factory configured to work with rs232 but we can't reach it on our system, it's just showing of offline status. In the ladders we had a special subroutine for modbus, including all the registers and status of the system, we are reaching these points but it doesn't work. I'll attach
Dear all, I'm programming an application on a SM43-J-R20 PLC+HMI. I've added a V100-17-RS4X card, in order to use RS485. I've succesfully implemented Modbus RTU communication with a Frequency Drive. The thing is, I need to communicate with 11 of them. The ladder logic so far uses the Modbus function blocks, as can be seen on the Modbus webinars on Unitronics page. That is, I SET a variable (ex:MB0) , which is used for enabling the "function 06 Modbus" block (preset holding register). At the output of the block, I RESET that same variable, ensuring the block gets execu