Search the Community
Showing results for tags 'store'.
The search index is currently processing. Current results may not be complete.
Hi there, I am trying to write my DataTable to SD card using Store DTI to file function, but always get an error. Error code -4, thus Internal Error. Contact support. So I have tried to download an official example, called Unistream_070_Indexed_Data_Table to the PLC, but it does not write the file as well, but the error code is -6 Write file error. I have tried SanDisk Ultra 16 GB and Kingston CanvasSelectPlus 16GB, both formatted to FAT I have also tried to Run UniApps, File Browser and copy some file from USB flash disk to SD card, that worked DataSampler files are written succesfully to the SD card and there is no problem So assuming the PLC recognizes the SD Card properly. Versions info: PLC bins: 1.30.51 from Oct-25-20 UniLogic version: 1.30.62 activated HW configuration: - PLC: US7-B5-B1 - UAG-CX-XKPLXXXX -UIA-00800N_0 -UID-W1616T_1 Note that the expansions cards are not physically connected to the PLC as I am developing the software on table, the plc will be included in the switchboard later Thx Jan
Hi. I'm need help for the function storage the date. Is possible to monitor the time when the output is up? My proccess need a logic for to monitor a output but the time can isn't reset when the output is down. I'm monitoring the useful life of lamp. The time need reset when a lamp is replaced. Is possible with V350-J-TR20?