Raymond Santiago Posted November 15, 2012 Report Share Posted November 15, 2012 Hi, I am new in UniOPC in Windows2003 operating system. Here is the scenario, I have a V350 OPLC that I am communicating in SCADA. I can monitor the OPLC value via Visilogic, but I cant see its value in SCADA. I think my problem is the UniOPC tool, it shows that the tag value has a bad quality. Does anyone have an idea how can I make UniOPC work in WIndows2003? Thanks. Best Regards, Raymond Santiago Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.