Michael Hickey Posted June 6, 2013 Report Share Posted June 6, 2013 Trying to get information from MF13 into a SCADA system. having trouble with the addressing. It appears that the addressing is in Hex starting at 4000h. So I've tried converting 4000h to decimal (163840 then added 400001 and then add 13 for a result of 56398. I am able to establish communications to the Floating point registers. I know that the communications works because i am moitoring regester MI0 to MI30 already. Any suggestions? Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.