RBC Posted January 7, 2014 Report Share Posted January 7, 2014 Hi. I've got an application at my client that have 5 stages running on preset timers. Now my client wants to be able to run the fans in forward and reverse direction. He want to set the percentage the fans must run in the reverse direction. Lets say the stage is 5hrs and he want to switch on the for/rev funtion. Then i must work out how much time is left of the timer on work out lets say 20% and put that value in the reverse timer. is it possible or must I change the timers to counters? Thanks for your help. Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.