Don2015 Posted March 16, 2017 Report Share Posted March 16, 2017 Ok, I thought it be better to start a new topic then to continue in the other one. I thought everything was going great but today I see the remote operator trying to do it's thing by trying to reconnect, but it just keeps looping without connecting, so I thought I better look into the PLC, and I added the V700 Ethernet read function and put in the value of #22 and got the output value of 23 which is good then I put the input to #21 and I got back the value of 20. That means any value other then 0 I'm supposed to check with Unitronics. Thanks, Don Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.