Edilson Adriano Lucas Posted July 30, 2019 Report Share Posted July 30, 2019 Hello my friends, I have some difficulties communicating with a power meter, it has a Floating Point 32 address, and I can't communicate. I performed tests on KepServer and got success and also with ModbusScan. You could be helping me set up the program or teach me some procedure you might be doing to establish communication. Attached is the list of registers. Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.