John Gioia Posted February 13, 2018 Report Share Posted February 13, 2018 Hi all, I have successfully configured TCP/IP on my V700. I have assigned it an internal IP address, SubNet Mask and Gateway and can ping my PLC from my computer. I was able to successfully use Remote Operator and import my .URC file and all is good. I used the default 20256 port number. I have asked the IT department to port forward port number #20256 to my internal IP address of my PLC so that I can attempt to test the Remote Operator from the outside internet world. I have defined the external IP address in my favorites in the Remote Operator with port #20256 and I have used the same PLC name that I defined in the PLC. I gave myself at least a 20 second timeout and I still cant seem to connect to my PCL remotely (outside of my office) .. have I missed out on something ? Regards John Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.