firstname.lastname@example.org Posted September 24, 2020 Report Share Posted September 24, 2020 Hello, It is a system created 5 months ago. A USP-104-B10 with 3 URB-TCP remote adapters located in different places in a plant. Those adapters collect information from machines and displaying on USP. Three days ago i have lost communication between modules. Since then i cannot restore thinks. My structure is Panel IP (192.168.188.88 for example), CPU IP (188.8.131.52 for example) , URB1 IP (184.108.40.206), URB2 IP (220.127.116.11) and URB3 IP (18.104.22.168). Eth. port1 on panel is connected to our network. Eth2. port is connected to Eth1. port on URB1, Eth2. port on URB1 goes to Eth1 on URB2 and so on. The problem was when i have to establish communication at the beginning. Difficulty was that i have different locations. It is very nice described how use BOOTP Server, but it doesnt work until i disconnect all URB adapters and put them side by side to USP. Only then it works. Can you explain how to do this without removing URB from their locations. Also another thing. Where can i find some detailed info for limitation of HMI Panels. I was surprised when UniLogic told me that i have max. 255 elements per screen on USP 104 . Is it the same for 7", 10 and 15" screens? And some suggestion about Graphs. It will be nice option to decide how big is visible area of the graph. At my case on screen 800x600 and limitation of minimum size 500x300 i can put only two graphs and they are not looking good with this big buttons and background for axes. Only suggestion, i know this is a hard thing to do. Thank you in advance. Quote Link to comment Share on other sites More sharing options...
Join the conversation
You can post now and register later. If you have an account, sign in now to post with your account.
Note: Your post will require moderator approval before it will be visible.